At Strittmatters, we are ready to meet all of your air conditioning, heating and plumbing needs in Denton, TX. Our highly trained, experienced technicians put a priority in you and your family’s comfort. We can service, repair, maintain and replace all makes and models of heating, cooling and plumbing equipment. The best part is that we charge the same great rate from 7 a.m. to 8 p.m. Whether we are there for 2 hours or 8 hours, you still pay the same price. Our flat-rate pricing allows you to choose the level of repair that works best for your budget. We also guarantee that we will go above and beyond to make sure you are satisfied.
Call us today to find out about our maintenance agreements and to schedule your precision tune-up for your air conditioning, heating and plumbing system.
(940) 566-1122 or (972) 436-6585
for Denton, TX
Our Reviews by City
Cheryl - Denton, TX
Strittmatter saved the day!!! Our capacitor went out on our home that’s not even 4 years old. It was 85 degrees inside and our builder’s A/C supplier wasn’t responsive or helpful so a neighbor suggested Strittmatter. I called about 6 pm and we have the issue fixed before 8:30 pm. And, they cost less than what the supplier was going to charge. Kyle was a pleasant and helpful young man who made suggestions for things that the builder should have done. So nice to have such a positive experience.
Mark - Denton, TX
On time, professional, clear communication, effective solution, good listening skills.
Sully - Denton, TX
Timely, very informative.
Trask - Denton, TX
Polite, diligent, great work
Great job - very professional service!
Cindy - Denton, TX
Mark - Denton, TX
Quick service, polite
Kyle - Denton, TX
Scott - Denton, TX
Excellent Customer Service
Brown - Denton, TX
Called on a Sunday because hot water heater was leaking. Was able to talk to someone and they came out the same day! Mo and his partner were honest and upfront about the repair! They replaced the hot water heater the same day, and even wrangled and killed a snake in the garage! No extra charge for pest control! Would recommend Strittmatter for all your plumbing needs!
Cobert - Denton, TX
Was Highly impressed and completely satisfied with the service and professionalism! Both individuals were billboard models of customer service!
Tim - Denton, TX
Durant - Denton, TX
Good guys providing excellent service
Trevino - Denton, TX
The two young men who came to the house arrived on time and were very nice, professional. We needed an old gas pipe removed from our deck. The we’re able to get the job done promptly. Two boards needed to be taken up, they removed the boards, removed the pipe, and cleaned up. I asked if they had time to look at a leaky faucet at the front of the house. They said sure and we’re able to fix it right away. I would not hesitate to recommend this company for any plumbing needs.
Wendy - Denton, TX
Mary - Denton, TX
Kyle was very thorough
Sue - Denton, TX
Anthony - Denton, TX
Cody was awesome!
morgan - Denton, TX
I was very appreciative of his explanation of each step he took while cleaning out our condensation issue. He wasn’t in a big hurry and easy to talk to. I give him a big thumbs up and hope that you give him our sincere thanks again. We will definitely call again for our needs due to our experience with Cody
Timely and quick.
Tom - Denton, TX
Very good service. Technician was friendly and helpful
June 8 tune up
Holly - Denton, TX
Victor was polite and pleasant.
Shannon - Denton, TX
This was my first experience with using this company, but I would not hesitate to use them again. Toby was knowledgeable, answered my questions, and made me feel comfortable about the repairs. Toby, Brandon, Mo, and Mike were thorough workers and kept me informed while doing the job. Reasonably priced and the work was done right. My new plumbing company!
Great service. Toby is a real professional.
Doris - Denton, TX
My water heater start leaking and I called Strittmatter immediately and they were at my house in less than thirty minutes. They installed a new water heater and did a great job.
Frances - Denton, TX
Always great service whether maintenance or a problem.
Really quick to fix 2 problems
James - Denton, TX
Called at 8, fixed by 1! Fast to arrive and fix 2 different problems. Very professional technicians. Second time we’ve used Strittmatter- excellent and fast response both times. They are our new plumbers now.
Mike - Denton, TX
Toby and Michael arrived 2 minutes early, and quickly diagnosed and repaired my issue at a very fair price. Both techs were polite, friendly, and got the job done quick enough for me to run off and go fishin'.
Replaced hose bib
Replaced hot supply line to water heater.
Installed 30 gallon electric Bradford White water heater.
Minor wire repair and replaced a contractor to get the A/c up and running
Drained 50 gallon water heater
Cleaned the condenser coil on a Rheem upflow system on 2 properties and added refrigerant as well, after repairs unit is working as designed and cooling efficiently
Ouote to rebuild trim in shower and install kitchen faucet.
Replaced shower trim and handle
Installed 1/3 hp disposal
Replaced hot side stem at tub faucet.
Replaced frost proof hose bib.
Plumbing tune up
Cleared condensate line on carrier heat pump system and after clearing line unit resumed normal function and is cooling as designed.
Did tune-up on one Lennox system and all operations were normal.
Checked system and found blower motor had lost bearing causing blower wheel to rub on housing. Replaced blower motor and tested system all operations returned to normal.
Checked system and found low on R-22. Recommended replacing condenser and coil and supply and return plenums and adding 4in filter base. Scheduled install.
Checked system and found t-stat wired improperly and rewired and checked filter and found impacted. Replaced filter and all operations returned to normal.
Checked system and found filter door off the unit allowing attic air to be sucked into system. found damper closed. Replaced filter door and opened damper. Checked Freon levels and found low on R-22. Added Freon and did leak search on evaporator coil. Recommended condenser and coil replacement.
Checked system and found dirty condenser coils and cleaned condenser. Checked Freon levels and system was over charged. Did heat load calculations and found system was to small for the area trying to cool. Removed ducts from upstairs rooms and added return air to ceiling in downstairs offices.
Checked system and found dead duel run cap. Replaced duel run cap and all operations returned to normal.
Checked system and found system froze up. Cleaned condenser coils and replaced air filters. Checked Freon levels after system thawed out and all operations returned to normal.
Checked system and found froze up. System had a restriction causing bad Freon pressures. Filter was clogged and not allowing proper air flow. Gave customer numbers to replace Condenser and Coil and scheduled install.